To be honest, I have never written comments or felt the need too, but in this instance I needed to make an exception. Two incredibly professional, polite and friendly gentlemen. The quality of the work was incredible, our house had recently been renovated and it wasn’t lost on them as they took care and appreciated the work already completed. Nathan was very knowledgable and gave us plenty of options which ended up being perfect for our needs. It’s a great addition to our home, and the way that Jack ran all the electrical and pipework is masterful, exceptionally tidy and very neat…
Duty share at NHS Hospital
Installation of 2 x systems for a W.I.C in the Pharmaceutical department with a duty share and emergency switch over.
NHS Hospital, London
2 x AFR evaporators
2 x J&E Hall condensers
1 x Duty share switch over panel
About the project
Part of a refurbishment project was to install a new walk in chiller within the pharmaceutical department of the hospital. The walk in chiller was designed with a switch over panel and duty share so one system would run at a time and switch over every week. The system has also been designed so if a high temperature has been detected due to a failure of one system, then the panel will switch the systems over to ensure the products within the coldroom stays at temperature. The project included a new box build as well as the new refrigeration system and panel.
Very pleased with work done & very professional.
Very impressed with their professionalism, their workmanship. They left the house and garden perfectly clean and tidy. Easy to understand demonstration on completion of installation. Super company that I would recommend to anyone.
Professional and efficient for my AC Service.
Phoenix ACR were really friendly and ensured I was happy throughout the work taking place. I am so glad I chose them to carry out the work. A professional friendly company who put the customer needs at the forefront of their priorities. A pleasure to have in the house. Thanks for a great job, highly recommended.
Great experience with Phoenix. Had three indoor units fitted in my property. They are very professional, discussed all available options with regards to units airpumps and outdoor units and helped me choose the best for my needs. Very professional and tidy. Was always on time on the job. Higly recommended and I am sure we will be in touch in the future to get more units sorted downstairs.
Excellent work carried out by Nathan, very professional, friendly and tidy. Will be getting him back to add to some more rooms.
Bedford - Bedfordshire
Just had an air con unit fitted into my bedroom which also does heating too! Could not be happier with it! Had several quotes from 3 different companies and this company were the best value! A lot of care and attention given and they made sure I was 100% happy with it. A* service! Will definitely use again. Thank you!
Work was done to a great standard on both days. When asked questions about what was going to happen and what was happening they were straight to the point and very informative. Cleaned as they went and polite all the time they were here working. Tested the equipment in front of me to show me how to use it.
All work carried out well and on time, unit works well and nice to have someone reliable to use for the future.